Install internal tooth Iockwasher (12) and nut (11) on terminal stud (8) and tighten against inside of
terminal board (13).
Observe identification tags when installing internal wires.
Slide flat washer (10) and terminal lug(s) of wire(s) (9) onto stud (8).
Install flat washer (7) and nut (6) on terminal (8) and tighten against wire terminal lug.
Position cover (4) on switch box (5) and secure with 16 screws (1), 16 Iockwashers (2) and 16 flat
b. Indicat or Light and Wire Assembly Repair and Replacement. (See figure 4-10.) There are two indicator
light and wire assemblies in the switch box. This procedure is typical for both. When attaching wires, refer to the
schematic inside the switch box (figure 4-7). The indicator light and wire assembly is repaired by replacing
defective terminals or soldering broken wires. Soldering shall be done in accordance with TB SIG 222.
Remove 16 screws (1), 16 Iockwashers (2) and 16 flat washers (3) securing cover (4) to switch box
(5) and take cover off switch box.
Remove screw (6), nut (7) and star washer (8) attaching each indicator light wire terminal (9) to its
respective switch terminal (10). Take power cable wire (11) and indicator light wire (12) off switch
Unscrew nut (13) and internal tooth Iockwasher (14) securing indicator light housing (15) to cover (4)
and slide nut and Iockwasher off wires (12).
Pull terminal (9) off each wire (12).
Pull out light and wires through cover (4).