ARMY TM 9-6115-639-13
AIR FORCE TO 35C2-3-386-51
MARINE CORPS TM 10155A-13/1
4-22. CIRCUIT INTERRUPTER INDICATOR LIGHT MAINTENANCE - cont.
Remove and replace any component that is
damaged to the extent that it will effect the safe
operation of the generator set.
Install CIRCUIT INTERRUPTER indicator light
(5, Figure 4-13) onto control panel (2) using
attaching nut (6) and lockwasher (1).
Remove bulb (3) from indicator light (5)
prior to soldering.
Connect electrical wiring to the rear of indicator
light (5) and secure using soldering iron. Using a
heat gun, adhere heat shrink tubing to wire
Screw indicator light bulb (3) into indicator light
(5). Install cap (4).
Close control panel (2) and lock in place using
quarter-turn fasteners (7).
Figure 4-13. CIRCUIT INTERRUPTER
Indicator Light (Sheet 2 of 2)