100 kW TACTICAL QUIET GENERATOR SET
CONTROL BOX ASSEMBLY MAINTENANCE
THIS WORK PACKAGE COVERS:
Tools and Special Tools
Metal jewelry can conduct electricity and become entangled in generator set components. Remove
all metal jewelry when working on generator set. Failure to comply can cause injury or death to
High voltage is produced when this generator set is in operation. Make sure unit is completely shut
down and free of any power source before attempting any repair or maintenance on the unit. Failure
to comply can cause injury or death to personnel.
DC voltages are present at generator set electrical components even with generator set shut down.
Avoid shorting any positive with ground/negative. Failure to comply can cause injury to personnel
and damage to equipment.
Replace Control Panel Lights On Electronic Modular Control Panel (EMCP)
On EMCP, set ENGINE CONTROL switch to OFF/RESET.
Set DEAD CRANK SWITCH to OFF.
Set Battery Disconnect switch to OFF.
Open control panel access cover and turn three captive retainers (1) and lower EMCP front panel (2).
Inspect wiring to lamps.
If wiring is broken, notify maintenance.
Close EMCP front panel (2) and secure with three captive retainers (1).