ARMY TM 9-6115-639-13
AIR FORCE TO 35C2-3-386-51
MARINE CORPS TM 10155A-13/1
If battery is not installed, ensure battery cable ends are isolated from
each other, and positive cable end is isolated from ground. Mounting
posts on generator set enclosure are provided for this purpose. Failure to
isolate battery cable ends can result in severe electrical discharge.
If auxiliary power is required, connect auxiliary power cable to SLAVE RECEPTACLE (6, Figure 2-
If auxiliary fuel source is to be used, perform procedure outlined in step l
k. Fill fuel tank as follows:
Fuel used in this generator set is flammable and toxic to skin, eyes, and
respiratory tract. Avoid repeated or prolonged contact. Handle only in
well ventilated area. Keep away from sparks, open flames, or other
sources of ignition. Do not splash fuel on hot components. Do not fuel
generator set while it is operating. Do not over fill the tank. Ensure the
unit is properly grounded before fueling. Failure to observe this warning
can result in personal injury and equipment damage due to potential fuel
ignition and possible explosion. Ensure approved gloves and face shield
are worn during handling.
Remove fuel fill cap (31, Figure 2-1) from fuel tank.
Connect a static ground line (provided with the fueling source) between generator set ground
stud and fueling source.
Fill fuel tank with up to 4 gallons of recommended fuel.
Remove static ground line and install fuel fill cap (31).