ARMY TM 9-6115-639-13
AIR FORCE TO 35C2-3-386-51
MARINE CORPS TM 10155A-13/1
If auxiliary fuel source is to be used, connect as follows:
Fuel used in this generator set is flammable and toxic to skin, eyes, and
respiratory tract. Avoid repeated or prolonged contact. Handle only in
well ventilated area. Keep away from sparks, open flames, or other
sources of ignition. Do not splash fuel on hot components. Do not fuel
generator set while it is operating. Ensure the unit is properly grounded
before fueling. Failure to observe this warning can result in personal
injury and equipment damage due to potential fuel ignition and possible
Remove auxiliary fuel cap (32, Figure 2-1) from auxiliary fuel connection.
Connect auxiliary fuel line to auxiliary fuel connection. Ensure proper fuel type is used.
2-7. INITIAL ADJUSTMENTS, DAILY CHECKS, AND SELF TEST.
Initial Adjustments. No initial adjustments are required for operation of the generator set.
b. Daily Checks. Perform all operator PMCS in accordance with Section II.
c. Self Test. To check the operational readiness of generator set protection devices and indicators,
perform the following procedure:
Ensure DC CIRCUIT BREAKER (9, Figure 2-3) is pushed in.
Ensure that EMERGENCY STOP switch (13) is pulled out.
Place START / RUN/ STOP switch (7) in RUN position.
Depress the FAULT RESET / PUSH TEST button (15) on the fault indicator module and the
CIRCUIT INTERRUPTER indicator (12) on the control panel to check indicators. All indicator
lights shall illuminate. If CIRCUIT INTERRUPTER indicator does not illuminate, replace
bulb. If any malfunction light does not illuminate, refer malfunction to Unit maintenance.
Place START / RUN/ STOP switch (7) in STOP position.
Repeat steps (1) through (3) to verify malfunction was corrected.