ARMY TM 9-6115-639-13
AIR FORCE TO 35C2-3-386-51
MARINE CORPS TM 10155A-13/1
a. Open load terminal cover to access load and ground terminals (1, 2, Figure 2-3). Connect load cables
in accordance with TERMINAL VOLTAGE nameplate mounted on the inside of cover (120/240 volts, 3 wire or
120 volts, 2 wire). Close terminal cover and lock.
Ensure voltage selector switch setting matches load cable voltage
connections. Mismatch will cause damage to equipment and may result
in injury to personnel.
b. Set voltage selector switch to match load cable voltage connections as follows:
Unlock generator set main access cover latches and lift cover to open.
Locate voltage selector switch access door (3) on top of power inverter / converter (4). Open
access door and place voltage selector switch in desired position (120/240 volts, 3 wire or 120
volts, 2 wire). Close and lock door.
Voltage selector switch access door (3) must be closed securely, or
generator set will not produce power.
Close generator set main access cover and lock using latches.
c. If auxiliary fuel source is connected, place the AUX FUEL switch (5) in the ON position.
d. If auxiliary power is required, connect auxiliary power cable to SLAVE RECEPTACLE (6).
If battery is not installed, ensure battery cable ends are isolated from
each other, and positive cable end is isolated from ground. Mounting
posts on generator set enclosure are provided for this purpose. Failure to
isolate battery cable ends can result in severe electrical discharge.
e. If ambient temperature is below +20F (-6.6C), refer to para. 2-14.