ARMY TM 9-6115-641-24
AIR FORCE TO 35C2-3-456-12
d. Refer to Figure 21 for minimum enclosure clearance measurement requirements and Figure 22 for base
2-2-2. Outdoor Installation.
Make use of natural protective barriers.
b. Allow space on all sides for service and maintenance, refer to Figure 21.
Ensure that site soil is firm and well drained.
Use planks or other material for support in areas where soil will not support the generator set.
2-2-3. Indoor Installation.
Exhaust discharge contains deadly gases. Do not operate generator sets in en-
closed areas unless exhaust discharge is properly vented outside. Severe per-
sonal injury or death due to carbon monoxide poisoning could result.