ARMY TM 9-6115-639-13
AIR FORCE TO 35C2-3-386-51
MARINE CORPS TM 10155A-13/1
Table 2-1. Operator Preventive Maintenance Checks and Services for MEP 831A / 832A
Not Fully Mission
a. Inspect for cracks, dents, and corrosion
in accordance with para. 3-5.
b. Inspect for loose or missing hardware.
Significant cracks in
any generator set
a. Inspect top lifting cover for security of
attachment in accordance with para. 3-5.
b. Inspect air intake and exhaust ducts for
obstructions and blockages. Clear
obstructions and check for damage.
Cover is not secure.
Latches do not lock,
allowing cover to
Intake or exhaust are
blocked, or damaged.
Control box and
a. Inspect for secure attachment. Check that
hinged panel is closed and locked.
b. Inspect switches, meters, indicators, and
terminals. Conduct fault lamp test by
depressing FAULT RESET / PUSH TEST
switch. Refer to para. 3-6.
c. Inspect electrical wires for damage, corr-
osion, or electrical short. Check for bent,
broken, or missing pins.
Any switch is not
operable or any meter
is damaged. Fault
indicator is defective
or lamp does not light.
Wires or connectors