(9) Unstrap and remove power cables from fenders of both power units.
When performing step 10, note that the power cables, the individual wires in the cables,
and the generator set load terminals are all marked for identification. Make certain these
markings correspond when connecting power cables.
(10) Connect power cable to each generator set load terminal board as follows:
White wire to load terminal L0.
Black wire to load terminal L1.
Red wire to load terminal L2.
Blue wire to load terminal L3.
Connect both power cables to switch box.
Do not operate power plant until both power units have been properly grounded
(paragraph 4-2, b.). Serious injury or death by electrocution can result from operating an
ungrounded power plant.
To avoid damage to equipment, make certain of voltage, frequency, and phase
requirements of load being connected to power plant.
Connect power plant switch box to system or equipment to be powered. Refer to TM 5-6115-465-12 and
generator set load terminal board data plate. Data plate is located on inside of generator enclosure door
nearest load terminals.
Remove quick-release pins securing both power unit personnel platforms and lower platforms.
On both power units, open control panel doors and the two doors immediately below the control panels.