Section IV. TROUBLESHOOTING
3-10. Power Plant Troubleshooting. There are no troubleshooting procedures authorized at operator
level for the power plant end item. Troubleshooting procedures for the individual generator sets and trailers are
contained in their respective technical manuals referenced below.
Generator Set Troubleshooting. Refer to TM 5-6115-465-12 for troubleshooting procedures applicable to
the generator set.
Trailer Troubleshooting. Refer to TM 9-2330-205-14&P for troubleshooting procedures applicable to the
Section V. OPERATOR/CREW MAINTENANCE
3-11. Fire Extinguisher Maintenance. The AN/MJQ-10A Power Plant is equipped with two 5 lb CO2fire
extinguishers. Maintenance is limited to weighing the fire extinguishers monthly to insure that they are sufficiently
charged. Fully charged, each fire extinguisher weighs 13 Ibs. Send the unit to specialized activity for recharging if
it weighs 12.5 lb or less.
Do not attempt to verify readiness of a fire extinguisher by partially discharging unit. Any
discharge of contents will require refilling.