Table 3-2. Operator/Crew Preventive Maintenance Checks and Services (PMCS) (cont).
B - Before
D - During
M - Monthly
Item to be inspected.
Procedure: check for and have repaired,
filled, or adjusted as needed
GENERATOR SET GAGES AND INSTRUMENTS
i. Check that all lights on fault indicator panel (24)
are out during operation. Check bulb operation
with TEST or RESET switch on panel.
Fill tank (25) upon completion of operation,
Fuel system temperature must be above
freezing when draining water and sediment.
Open drain (26) and drain water and sediment
from fuel tank into a suitable container. Allow to
drain until fuel runs clean.
Equipment is not
Fault light will not go out
when switch is set to TEST
or RESET position, then
released. All bulbs should
be lit when switch is in TEST
or RESET position.