a. 60 Amp Circuit Breaker.
(1) Tag and identify leads.
(2) Loosen three screws (4, Figure 4-8) and remove leads.
(3) Remove three screws (4).
(4) Raise circuit breaker (6) approximately 35 degree angle and remove from under breaker mounting rail (7).
(5) Remove nine remaining circuit breakers, repeat steps (1) through (4), above.
a. Hold circuit breaker (6) at 35 approximately degree angle and install to under breaker mounting rail (7).
b. Install three screws (4). Tighten screws.
c. Install three leads and tighten screws (4). Remove tags.
d. Install three remaining circuit breakers, repeat steps a through c above.