Open access panel and remove by sliding off of hinges. Remove dust covers (1, Figure 2-4) and stow inside
22.214.171.124 Observe cable marking and route through entry bushing (2) to TB1 or TB2, as required. Observe cable markings
and connect PHASE A (L1) to TB1 -A, PHASE B (L2) to TB1 -B, PHASE C (L3) to TB1 -C, NEUTRAL (LO) to TB1 -N
and GROUND to TB1 -G. Torque set screws in accordance with Appendix H.
126.96.36.199 Install access door by sliding onto hinges, then dose door.
2.4.8 Grounding the Power Distribution Panel. Grounding of the power distribution panel is through the generator set
ground rod and ground cable.
2.5 OPERATING PROCEDURES.
High voltage is present in this equipment during operation. Make certain all unused
connectors are covered to prevent electrical shock Death serious injury may result
Never block circuit breaker switches in the ON position. Excessive current will
Make certain upper door assemblies are dosed and secured to prevent rain water
from entering power distribution panel.
Refer to applicable technical manuals and FM 2031 for operating procedures for the
power generation equipment in use.
High Voltage is present in this equipment during operation. Before turning on electrical
power, alert all users. Failure to observe this warning could result in serious injury or
Set both main circuit breakers to the OFF position.
Set All branch circuit breakers to the OFF position.
Refer to applicable TM for operating procedures and start the generator set.
Set main circuit breaker to ON position.
Observe DS1, DS2, and DS3, for indication of power at power distribution panel.
One by one, set circuit breakers for branch circuits being used to ON position.