ARMY TM 9-6115-639-13
AIR FORCE TO 35C2-3-386-51
MARINE CORPS TM 10155A-13/1
4-51. AUXILIARY FUEL PUMP MAINTENANCE - cont.
Inspect auxiliary fuel pump and fuel strainer for cracks, corrosion, evidence of leakage, and obvious
Inspect fuel hoses for cuts, cracks, or other damage.
Inspect fuel fittings for crossed, stripped, or damaged threads.
Inspect electrical wiring for cuts, crimps, bare wire, or other damage. Ensure terminal lugs are securely
Remove and replace any component that is damaged to the extent that it will effect the safe operation of
the generator set.
Apply teflon tape to threads of all fitting prior to installation.
Install elbow (14, Figure 4-46), washer (15), nut (16), and cap (17) onto fill pocket (8). Connect fitting
(13) to elbow (14).
Install elbow (12) and fuel strainer (6) into auxiliary fuel pump (7).
Mate auxiliary fuel pump (7) to fill pocket (8) and secure using two screws (9), washers (10), and locknuts
Connect fuel hose (4) to fuel strainer (6) and fitting (13). Secure by tightening clamps (5).
Connect fuel hose (1) to elbow (12). Secure by tightening clamp (2).
Close main access cover and lock in place using latches.