Table 4-1. Unit Preventive Maintenance Checks and Services (PMCS). CONT.
H Hours of operation
S - Semiannually
Item to be
Fuel Strainer and
Before performing any maintenance
that requires climbing on or under
trailer, set trailer handbrakes, chock
wheels, and lower rear leg prop.
Injury to personnel could result
from trailer suddenly rolling or
Generator set checks and services in
this table are described as performed
on a single generator set. These
procedures must be performed
on each of the two generator sets
that make up the AN/MJQ-16.
Inspect generator set for fuel and oil
leaks, loose or missing components and
hardware, and unusual wear or
deterioration. Clean generator set.
Fuel system must be above freezing
temperature when draining water
and sediment from strainer, filters,
Open drains on fuel strainer, and
secondary filters. Drain water and
sediment (table 3-2, TM 5-61 15-584-12)
Allow to drain until fuel runs clean.
Open drain on fuel tank and drain water
and sediment (table 3-2, TM 5-6115-
584-12). Allow to drain until fuels runs