UNIT (FIELD) LEVEL MAINTENANCE
TACTICAL QUIET GENERATOR 200 kW, 50/60 Hz MEP-809A/PU-809A
PMCS, INCLUDING LUBRICATION INSTRUCTIONS
Metal jewelry will conduct electricity. All jewelry can become entangled in generator set
components. Remove all jewelry when working on generator set. Failure to comply can cause
injury or death to personnel by electrocution.
DO NOT wear loose clothing when performing checks, services and maintenance. Failure to
comply can cause injury or death to personnel.
High voltage is produced when this generator set is in operation. Make sure unit is completely shut
down and free of any power source before attempting any repair or maintenance on the unit.
Failure to comply can cause injury or death to personnel.
High voltage is produced when the generator set is in operation. Never attempt to start or
maintain the generator set unless it is properly grounded. Failure to comply can cause injury or
death to personnel.
Table 1. Preventive Maintenance Checks and Services.
ITEM TO BE
100 kW TQG
Change engine oil and oil filter
Engine oil change/
filter change not
Perform quarterly PMCS
Any failed inspection.
Check the entire housing, to include
Any doors, panels,
doors, panels, latches, and hinges, for
latches, or hinges
damage, missing parts, and secure
damaged, loose, or
mounting. Check mounting points for
rust or corrosion and loose or missing