Table 1. Operator Troubleshooting Continued.
TEST OR INSPECTION
9. Convenience receptacle on
4. Under GROUND FAULT
If TEST window is not red when TEST
is pressed, notify maintenance.
panel has no power. Continued
nameplate, press TEST pushbutton
on GFCI circuit breaker.
5. Press RESET pushbutton on GFCI
If TEST window is not clear when
RESET is pressed, notify
6. Check load is no more than 15A and
If load is greater than 15A, reduce size
for possible ground fault
of load. If no ground fault or
overload exists, plug equipment
back into convenience receptacle.
10.Winterization kit (issued to selected
1. On FUEL FIRED HEATER
If switch is OFF, set to ON.
units only) is not operating. Red
CONTROL panel, press CIRCUIT
DIAGNOSTIC light is on.
BREAKER and verify that switch is
set to ON and indicator is lit.
2. Push press-to-test HEATER
If indicator does not light, notify
3. Verify red DIAGNOSTIC light is
Set CIRCUIT BREAKER switch to
OFF and notify maintenance.
END OF TASK