OPERATION UNDER USUAL CONDITIONS Continued
OPERATING PROCEDURES Continued
On GSP keypad (7), press AC METER (9) to ensure voltage and frequency are still at rated values. Adjust if necessary.
10. Press POWER METER (10) on keypad and cycle through each phase position while observing current readings. If
more than rated load is indicated in any phase, reduce load.