100 kW TACTICAL QUIET GENERATOR SET
ENGINE FUEL SYSTEM MAINTENANCE Continued
Fuel Tank Service
Fuels used in the generator set are flammable. When filling the fuel tank, maintain metal-to-metal
contact between filler nozzle and fuel tank opening to eliminate static electrical discharge. Failure
to comply can result in flames and possible explosion and can cause injury or death to personnel
and damage to the generator set.
Hot engine surfaces from the engine and generator circuitry are possible sources of ignition. When
hot refueling with DF-1, DF-2, JP5 or JP8, avoid fuel splash and fuel spill. Do not smoke or use
open flame when performing refueling. Remember PMCS is still required. Failure to comply can
result in flames and possible explosion and can cause injury or death to personnel and damage to
the generator set.
Fuel tank holds 66 gallons (250L).
The TQG can be refueled while it is operating without stopping the engine and allowing the TQG to cool
down. If you are hot refueling, Step 1 is not required.
On EMCP, set ENGINE CONTROL switch to OFF/RESET.
Remove fuel cap (1).
Remove filler tube with strainer (3); clean strainer as necessary and reinstall in filler neck (2).
To prevent damage to the diesel engine, use only specified diesel fuel to service the fuel tank. To
prevent condensation of water in fuel tank, always keep level at full. Refer to Table 1 for
Add diesel fuel to fuel tank per Table 1.
Install fuel cap (1).