Figure 4-3. Installing Power Unit.
To avoid damage to equipment, make certain of voltage, frequency, and phase
requirements of load being connected to generator set.
(6) Refer to data plate on load terminal board cover and to TM 5-6115-584-12. Connect power unit to
system or equipment to be powered.
b. Grounding. Check that generator set is grounded to GROUND TERMINAL stud on trailer body. Using
ground wire supplied with power unit, connect power unit to a suitable ground as described below. The following
sources of good ground are listed in order of preference.
As a substitute for the supplied ground wire, any copper wire of a least No. 6 AWG may