Start one power plant generator set and bring generator up to rated speed, voltage,
Set generator set circuit breaker to ON position.
Set associated switch on switch box to ON position.
When the power plant generator set in operation must be shut down, follow
steps (6) thru (10) to continue to supply power to system or equipment being
Start second power plant generator set and bring generator up to rated speed, voltage,
Set generator circuit breaker to ON position.
At switch box, set switch associated with first generator set to OFF position.
Set switch box switch associated with second generator set to ON position.
Shut down first power plant generator set.
c. Trailer Operating Procedures. Refer to TM 9-2330-205-14&P for specific operating
procedures for the M200A1 trailer.
Section Il. OPERATION OF AUXILIARY EQUIPMENT
Operation of Auxiliary Equipment. There is no auxiliary equipment supplied with the power plant.
Section Ill. OPERATION UNDER UNUSUAL CONDITIONS
2-3. Operation Under Unusual Conditions. When operating the power plant under unusual conditions
such as extremes in temperature or difficult terrain, there are steps that must be taken to protect the
a. Refer to TM 5-6115-545-12 for special procedures when operating the generator set under
b. Refer to TM 9-2330-205-14&P for special procedures when operating the trailer under unusual