Parts Required -
1. Fuse Holder, Qty. 1 (ea)
2. Splice, Crimp Type, Qty. 2 (ea)
3. Fuse, 3 Amp/250V AC, Time Delay, MDL-3, Qty. 1 (ea)
6.2.5 Repair Procedures:
a) Ensure generator set is shut down. Disconnect negative battery terminal.
b) Locate A1, terminal 8, wire # 106B (the A1 is mounted right-center on the back wall inside of the
c) From terminal 8, follow wire # 106B back six inches from terminal 8 (remove wire ties as
necessary.) Cut wire # 106B at point six inches from terminal 8. Leave the six inches of wire and
terminal attached to terminal 8.
d) Locate fuse holder (index 1 above.) Strip both wire ends; crimp a splice (index 2 above) on both
e) Strip exposed ends of wire # 106B; crimp one fuse holder lead splice to each end of wire # 106B.
Fuse holder should now be inserted in series with wire # 106B.
f) Install fuse (index 3 above) in fuse holder. Secure fuse holder and leads with wire ties as
g) Reconnect negative battery terminal
h) Modification complete
a) Start and run generator set.
c) Shut down set
d) Repeat steps a and step b.
e) Load test generator