2.7 OPERATION OF AUXILIARY EQUIPMENT
Power Generation Equipment. Refer to the Modified Table of Organization and Equipment (MTOE) for a listing
of generator sets used to supply power to the power distribution panel. Refer to the applicable TM and to FM 20-31 for
DISE Equipment. Refer to TM 946150-226-13 for operating instructions for the various components of DISE
equipment used with the power distribution panel.
2.8 PREPARATION FOR MOVEMENT.
High voltage is present in this equipment during operation. Do not attempt to disconnect
the equipment with electrical power on. Failure to observe this warning could result in
serious injury or death.
Dirt and contamination may plug connector sockets. Secure cap on connectors when
dissembling the equipment
Shut down the power distribution panel. Refer to paragraph 2.5.4.
Starting at the user's end, disconnect power cables and cover cable connectors.
At the power distribution panel, disconnect power cables, cover cable connectors, and coil cables.
Disconnect input power cables from power distribution panel and generator(s) and coil cables and install all
electrical connector covers.
Perform the after preventive maintenance checks and services in Table 2-1.
Install caps on output connectors, dose iower doors and top cover, and secure al latches.
SECTION IV. OPERATION UNDER UNUSUAL CONDITIONS
2.9 OPERATION IN EXTREME COLD
Do not touch cold metal parts with bare hands. Frostbite can cause permanent injury.
This equipment is designed for operation at temperatures as low as -25°F (-320C).
Cap unused connectors to protect against moisture.