100 kW TACTICAL QUIET GENERATOR SET
OPERATION UNDER USUAL CONDITIONS Continued
ASSEMBLY AND PREPARATION FOR USE Continued
Installation of Load Cables
High voltage is produced when this generator set is in operation. Make sure unit is completely shut
down and free of any power source before attempting any repair or maintenance on the unit.
Failure to comply can cause injury or death to personnel.
High voltage is produced when the generator set is in operation. Never attempt to connect or
disconnect load cables while the generator set is running. Failure to comply can cause injury or
death to personnel.
A qualified technician must make the power connections and perform all continuity checks. The
power source may be a generator or commercial power. Failure to comply with this warning can
result in injury or death to personnel.
When using single phase connections, balance loads between terminals. Do not connect all loads
between one terminal and N. Failure to observe this caution can result in damage to equipment.
On Electronic Modular Control Panel (EMCP), set ENGINE CONTROL switch to OFF/RESET (WP 0005 00-1).
Open rear left housing door and set DEAD CRANK SWITCH to OFF (WP 0005 00-13).
Open battery compartment and set Battery Disconnect Switch to OFF (WP 0005 00-15).
Select required output terminals from Table 1.
Open output load terminal door on rear right of housing.
Using terminal nut wrench (7) loosen terminal nuts (13) on output load terminals (14) selected in step 5.
Insert ends of load cables (15) through OUTPUT CABLES boot (8). Insert ends of cables into slots of output load
Tighten load terminal nuts (13) using terminal nut wrench (7).
10. Secure wrench (7) inside load terminal board door and close door.