DESCRIPTION AND USE OF OPERATOR CONTROLS AND INDICATORS Continued
RESISTOR ASSEMBLY A7
Table 5 describes controls located on resistor assembly A7. Resistor assembly A7 is located inside the control box assembly
behind the EMCP.
Table 5. Resistor Assembly A7 Controls.
CONTROL OR INDICATOR
Two-position switch. Used for frequency stabilization circuits and TQG
Up position used for generator constant 50/60 Hz operation.
Down position will accommodate fluctuations for under load conditions.
DC CONTROL POWER
When pushed in, circuit breaker supplies 24 Vdc power to GSC.