Table 3-2. Operator/Crew Preventive Maintenance Checks and Services (PMCS) (cont).
B - Before
D - During
A - After
W - Weekly
M - Monthly
Item to be inspected.
Procedure: check for and have repaired,
filled, or adjusted as needed
GENERATOR SET GAGES AND INSTRUMENTS
e. Check engine oil pressure gage (30) for normal
operating pressure of 25 psig.
Fill fuel tank (31).
Fuel system temperature must be above
freezing when draining water and sediment.
Open drain (32) and drain water and sediment
from fuel tank into a suitable container. Allow to
drain until fuel runs clean.
Equipment is not
Oil pressure drops below