Figure 4-3. Installing Power Unit.
To avoid damage to equipment, make certain of voltage, frequency, and
phase requirements of load being connected to generator set.
(6) Refer to data plate on load terminal board cover and to TM5-6115-585-12. Connect power
unit to system or equipment to be powered.
b. Grounding. Check that generator set is grounded to GROUND TERMINAL stud on trailer body.
Using ground wire supplied with power unit, connect power unit to a suitable ground as described
below. The following sources of a good ground are listed in order of preference.
As a substitute for the supplied ground wire, any copper wire of at least No. 6
AWG maybe used.