WIRING HARNESS MAINTENANCE.
This task covers:
Tool Kit, General Mechanic's
Generator shut down, TM 9-6115-645-10, Paragraph 2-9.2
Do not attempt any tasks inside generator housing with generator set
running. Failure to observe this warning could result in severe personal
injury or death.
Inspection is limited to visual inspection of components. Check for damaged and frayed wiring.
Test wiring for continuity (refer to Figure 4-27). Replace any open or broken wires or connectors.
Prior to removal, tag all leads on wiring harness.
Disconnect all leads and plugs. Remove wiring harness.
Repair consists of replacing wires, connectors, and terminals. Follow standard shop practice when performing all repairs.
Perform steps 1 thru 2 of removal.
Perform steps 1 thru 2 of installation, substituting new wiring harness for the defective one.
Position wiring harness in place.