TROUBLESHOOTING USING DVR FAULT CODES - Continued
CORRECTIVE ACTION - Continued
If problem not resolved, perform VOLTAGE rheostat test (WP 0040).
Verify that correct parameters are entered in DVR and that parameters match the
Enter proper parameters (WP 0085). Verify parameters after entry.
With generator set running, measure AC voltage between pins A3-26 and A3-28,
A3-28 and A3-30, and A3-26 and A3-30 per FO-4, sheet 3.
If voltages not 95 to 120 Vac at all three locations, shut down generator set.
Check fuses F1-10A, F2-10A, F3-10A and replace defective fuses.
a. Open fuse holder F1, F2, and F3.
b. Check resistance, F1-1 to F2-1, F2-1 to F3-1, and F3-1 to F1-1. Resistance
should be less than 1 ohm. If open or above 1 ohm, troubleshoot wires
Check resistance, F1-2 to F2-2, F2-2 to F3-2, and F3-2 to F1-1. Resistance
should be between 0.2 to 0.4 ohms. If open or above 0.4 ohms, troubleshoot
wires between F12, F2, and F3 and transformer PT2 and PT3, and
transformer primary winding, PT2, PT3 before removing wires from A3-26,
A3-28, and A3-30.
Check resistance, A3-26 to a3-28; A3-28 to A3-30, and A3-30 to A3-26.
Resistance should be between 0.2 and 2.0 ohms. If open or above 2 ohms,
troubleshoot secondary winding of PT2 and PT3 and wires between A3-26,
A3-28 and A3-30 to PT2 and PT3.
Measure AC voltage between pins A3-20 and A3-22, A3-22 and A3-24, and
A3-20 and A3-24.
Voltages should be the same and at the proper ratio to the output voltage in
accordance with parameter :02. If not, test generator (WP 0096).
If the problem is not resolved, replace DVR (WP 0041).
If operating in parallel, re-parallel the generator sets in accordance with
Start generator set and verify that problem has been resolved with no load.
If the problem does not exist with no load, verify that generator set is not
overloaded. Reduce load below rated generator set load.