ARMY TM 9-6115-672-14
AIR FORCE TO 35C2-3-444-32
MARINE CORPS TM 09244A/09245A-14
TABLE 2-5. OPERATOR PREVENTIVE MAINTENANCE CHECKS AND SERVICES (PMCS)
Check for and have
repaired or adjusted
Inspect air cleaner assembly and piping
for loose or damaged connections.
Check restriction indicator for indication
of clogged air cleaner element (Refer to
Clogged element is
DC voltages are present at generator
set electrical components even with
generator set shut down. Avoid
shorting any positive terminal with
ground/negative. Failure to comply
can cause injury to personnel and
damage to equipment..
Batteries give off a flammable gas. Do
not smoke or use open flame when
performing maintenance. Failure to
comply can cause injury or death to
personnel and equipment damage due
to flames and explosion.
Battery acid can cause burns to
unprotected skin. Avoid contact with
battery acid. Failure to comply can
cause injury to personnel.
Inspect electrolyte level (wet cell
Electrolyte level is
below battery plates.
Inspect cables and connectors for
corrosion and loose, damaged, or
Battery cables are
loose, damaged, or