ARMY TM 9-6115-672-14
AIR FORCE TO 35C2-3-444-32
MARINE CORPS TM 09244A/09245A-14
b. Allow space on all sides for service and maintenance. Refer to Figure 2-5 for minimum clearance
c. Ensure soil is firm and well drained.
d. Use planks or other material for support in areas where soil will not support the generator set.
Exhaust discharge contains deadly gases including carbon monoxide. Do
not operate generator set in an enclosed area unless exhaust discharge is
properly vented outside. Failure to comply can cause injury or death to
Never position generator set with air inlets near a wall or other object that
interferes with cooling air circulation. Failure to comply can cause damage
a. Provide ducts and vents to outside of building if good supply of cooling air is not available.
b. Make air intake and outlet openings in building same size or larger than those on the generator set.