Table 3-2. Operator/Crew Preventive Maintenance Checks and Services (PMCS) (cont).
B - Before
D - During
A - After
W - Weekly
GENERATOR SET GAGES AND INSTRUMENTS
Check that all lights on FAULT INDICATOR
panel (26) are out during operation. Check
bulb operation with TEST or RESET switch
Do not smoke or use open flame in the
vicinity of the power unit while refueling
a. Fill set tank upon completion of operation.
Fuel system temperature must be above
freezing when draining water and sediment.
b. Remove cap (27), open drain (28) and drain
water and sediment from fuel tank into a suitable
container. Allow to drain until fuel runs clean.
Fault light will not go out
when switch is set to TEST
or RESET position, then
released. All bulbs should
be lit when switch is in TEST
or RESET position.