Table 3-2. Operator/Crew Preventive Maintenance Checks and Services (PMCS) (cont).
B - Before
D - During
A - After
W - Weekly
M - Monthly
Item to be inspected.
Procedure: check for and have repaired,
filled, or adjusted as needed
GENERATOR SET GAGES AND INSTRUMENTS
Check that A.C voltmeter (23) indicates desired
output voltage as determined by load connec-
tions and amps-volts selector switch.
Check engine oil pressure gage (24) for
20 to 55 psig indication.
Check coolant temperature gage (25) for
170° to 200°F (76.7° to 93.3°C) indication.
Equipment is not
Desired voltage cannot be
obtained and maintained.
Oil pressure drops below
Temperature exceeds 200°F