Section II. OPERATION OF AUXILIARY EQUIPMENT
2-2. Operation of Auxiliary Equipment. There is no auxiliary equipment supplied with the power unit.
Section III. OPERATION UNDER UNUSUAL CONDITIONS
2-3. Operation Under Unusual Conditions. When operating the power unit under unusual conditions such
as extremes in temperature or difficult terrain, there are steps that must be taken to protect the equipment.
Refer to TM 5-6115-465-12 for special procedures when operating the generator set under unusual
Refer to TM 9-2330-247-14&P for special procedures when operating the trailer under unusual
2-4. Operation Under Emergency Conditions. When low fuel is indicated on primary power unit and
standby unit fails to start, follow the procedures below to enable primary power unit to use standby unit fuel
Set primary generator set fuel selector valve to SET TANK position.
Remove 25-foot auxiliary fuel line from standby generator set.
Disconnect fuel lines from both generator sets at auxiliary fuel connection.
Connect adapter on 25-foot auxiliary fuel line to connector on 25-foot auxiliary fuel line. Connect
other end of adapter to auxiliary tank fuel line on standby generator set. Connect other end of auxiliary fuel line
to auxiliary tank fuel fitting on primary generator set.