Table 3-2. Operator/Crew Preventive Maintenance Checks and Services (PMCS) (cont).
Item To Be Inspected,
Equipment Is Not
Procedure: Check For And Have
Repaired, Filled, or Adjusted As Needed
GENERATOR SET EXTERIOR
a. Check on, around, and beneath generator set
A Class III coolant or lubrica-
for fuel or oil and coolant leaks.
tion oil leak or any class fuel
leak is detected.
b. Check that generator set ground is properly
Not properly grounded.
installed and grounding connections are tight.
c. Manually open and close radiator louvers to
Louvers do not operate
check for proper operation.
Check for loose connectors on P3 Power/Control
Connector(s) cannot be
cable (1) at adapter plate assembly and PDU.
tightened, are damaged, or
Check for loose connectors on Power/Control
are missing parts.
cable (2) at PDU and ICC/CRG. Check for loose
connectors on Control cable (3) at PDU and
ICC/CRG. Check for loose connectors on
auxiliary cable (4) at PDU and standby generator
adapter plate assembly.