ARMY TM 9-6115-644-24
AIR FORCE TO 35C2-3-446-12
MARINE CORPS TM 09249A/09246A-24/2
Connect negative battery cable and close battery access door.
FIGURE 2-11. Control Panel Lights
2-22 SYNCHRONlZlNG LIGHTS.
Inspect synchronizing lights for cracks, corrosion, evidence of shorting, and other damage.
Shut down generator set.
Open battery access door and disconnect negative battery cable.
Release control panel by turning two fasteners and lower control panel slowly.
Tag and disconnect synchronizing lights (13, FIGURE 2-11) electrical connections.
Remove nuts (11) and washers (12).
Remove synchronizing lights (13) from control panel.
Unscrew lenses (14) and remove lamps (15) from light receptacles (13).