ARMY TM 9-6115-644-24
AIR FORCE TO 35C2-3-446-12
MARINE CORPS TM 09249A/09246A-24/2
Install control box top panel, paragraph 2-15-4.
d. Connect negative battery cable. Close battery access door.
2-20 PANEL LIGHTS.
Inspect panel light holder and directional cap for cracks, corrosion, stripped threads, and other damage.
Shut down generator set.
Open battery access door and disconnect negative battery cable.
Release control panel by turning two fasteners and lower control panel slowly.
Tag and disconnect panel light (1, FIGURE 2-11 ) electrical leads.
Remove nut (2) and washer (3).
Remove panel light (1) from control panel.
Remove panel light directional cap (4, FIGURE 2-11 ) from panel light housing (1).
Remove panel light bulb (5).
Install panel Iight bulb (5, FIGURE 2-11) into panel light housing (1).
Install panel light directional cap (4).