Table 3-2. Operator/Crew Preventive Maintenance Checks and Services (PMCS) CONT.
B - Before
D - During
A - After
W - Weekly
M - Monthly
This PMCS table lists the checks
and services as performed on a
single power unit. These pro-
cedures must be duplicated on
each of the two power units that
make up the AN/MJQ-15.
Perform weekly as well as before
You are the assigned operator but
have not operated the equipment
since the last weekly inspection.
You are operating the equipment
for the first time.
GENERATOR SET EXTERIOR
Check on, around, and beneath
generator set for fuel or oil and
Check that generator set ground is
properly installed and grounding
connections are tight.
Manually open and close radiator
louver doors to check for proper
Check fuel gage (1) for sufficient fuel for
A Class Ill coolant or
lubrication oil leak or
any class fuel leak is