Table 3-2. Operator/Crew Preventive Maintenance Checks and Services (PMCS) CONT.
Item to be inspected.
Procedure: check for and
have repaired, filled, or
adjusted as needed
GENERATOR SET GAGES AND
Check that all lights on fault in-
dicator panel (24) are out during
operation. Check bulb operation
with TEST or RESET switch on panel.
Fill tank (25) upon completion of
Fuel system temperature must be
above freezing when draining
water and sediment.
Open drain (26) and drain water and
sediment from fuel tank. Allow to drain
until fuel runs clean.
Equipment is not
Fault light will not go
out when switch is set
to TEST or RESET
position, then re-
leased. All bulbs
should be lit when
switch is in TEST or