PREVENTIVE MAINTENANCE CHECKS AND SERVICES (PMCS), INCLUDING LUBRICATION
Table 1. Preventive Maintenance Checks and Services Continued.
When running, winterization heater has
hot metal surfaces that will burn flesh
and allow heater to cool before
performing maintenance. Wear gloves
and additional protective clothing as
required. Failure to comply can cause
injury or death to personnel.
If the TQG is operating continuously, do
the DURING PMCS checks every four
Inspect fuel system for leaks, damaged,
Any fuel leaks,
loose or missing parts.
damaged, loose or
Inspect lubrication system for leaks,
Class III leaks.
damaged, loose or missing parts.
Damaged, loose or
Oil level is below hot
add oil mark on
Cooling system operates at high
temperature and pressure. When
performing DURING PMCS, wear
gloves and additional protective
clothing and goggles as required.
Contact with high pressure steam
and/or liquids can result in burns and
Check for unusual noise being emitted from
Cooling fan is
damaged or loose.
Check coolant level between COLD and
Coolant level is below
HOT lines in overflow bottle