200 kW TACTICAL QUIET GENERATOR SET
PREVENTIVE MAINTENANCE CHECKS AND SERVICES (PMCS), INCLUDING LUBRICATION
Table 1. Preventive Maintenance Checks and Services Continued.
Ground Rod Cable
High voltage is produced when this
generator set is in operation. Make sure
unit is completely shut down and free of
any power source before attempting any
repair or maintenance on the unit.
Failure to comply can cause injury or
death to personnel.
Inspect ground rod, grounding cable to
Any missing or
trailer terminal, and grounding cable to
Connections are loose
breaks, damage and corrosion.
Inspect accessory box clamping hatch hasp
and rivets for rust, corrosion and wear.
Check accessory box contents to ensure that
Ground rod and
all required items are present and
flammable. Do not smoke or use open
flames when performing maintenance.
Failure to comply can result in flames
and possible explosion and can cause
injury or death to personnel and
damage to the generator set.
Open battery access doors and inspect fuel
Any fuel leaks,
lines to fuel-fired heater for leaks,
damaged, loose, or
damaged, loose or missing parts.
Check hoses for leaks or cracks.
Class III leaks.
Verify that coolant shutoff valves on engine
Shutoff valves are not