200 kW TACTICAL QUIET GENERATOR SET
PREVENTIVE MAINTENANCE CHECKS AND SERVICES (PMCS), INCLUDING LUBRICATION
Table 1. Preventive Maintenance Checks and Services Continued.
GSC indicator lights
Touch LAMP TEST on keypad and check
that all eight indicator lights on GSC and
segments do not
upper and lower display segments light.
Alarm Module lights
Press LAMP TEST and check that alarm
do not light and
indicators light and alarm sounds.
alarm does not
missing or cable and
inspect parallel cable for damage.
Ground Rod Cable
High voltage is produced when the
generator set is in operation. Never
it is properly grounded. Failure to
comply can cause injury or death to
Any missing or
Inspect ground rod and cable for loose
connections, breaks, damage and
If generator set is trailer-mounted (PU-
809A), check to ensure identification
plates on trailer are secure.
Fire extinguishers are
Verify that two fire extinguishers mounted
not present or not
to trailer brackets and fully charged.
certified. Needle is
Check that fire extinguisher needle (if
not in green zone.
applicable) is in green zone.
Check fire extinguisher seal. If seal is
broken or missing, replace fire
Visually inspect bracket for obvious