200 kW TACTICAL QUIET GENERATOR
Table 1. Operator Troubleshooting Continued.
TEST OR INSPECTION
6. Alarm module OVERCURRENT
9. Press LAMP TEST on alarm
amber indicator flashes. TQG
module to reset overload fault
disconnects from load. Continued
10. Start and operate TQG
1. Monitor TQG for further problems.
2. If there is no identifiable problem
with the load and alarm recurs,
Metal jewelry can conduct electricity and become entangled in generator set components. Remove
all metal jewelry when working on generator set. Failure to comply can cause injury or death to
High voltage is produced when this generator set is in operation. Make sure unit is completely shut
down and free of any power source before attempting any repair or maintenance on the unit. Failure
to comply can cause injury or death to personnel.
DC voltages are present at generator set electrical components even with generator set shut down.
Avoid shorting any positive with ground/negative. Failure to comply can cause injury to personnel
and damage to equipment.
7. Alarm module GENERATOR
1. Set ENGINE CONTROL switch to
OVERLOAD amber indicator
flashes. TQG disconnects from
2. Set DEAD CRANK SWITCH to
3. Set Battery Disconnect Switch to
4. Check load connected to TQG to
Repair cause of overload or notify
see if there was a problem there that
could cause TQG to overload.
5. Determine if load is too large for
Reduce load below output capacity of
generator set. (Power requirement
cannot be larger than TQG rating.)
6. Determine if load has been
Reduce load as necessary.