200 kW TACTICAL QUIET GENERATOR
Table 1. Operator Troubleshooting Continued.
TEST OR INSPECTION
Metal jewelry can conduct electricity and become entangled in generator set components. Remove
all metal jewelry when working on generator set. Failure to comply can cause injury or death to
High voltage is produced when this generator set is in operation. Make sure unit is completely shut
down and free of any power source before attempting any repair or maintenance on the unit. Failure
to comply can cause injury or death to personnel.
DC voltages are present at generator set electrical components even with generator set shut down.
Avoid shorting any positive with ground/negative. Failure to comply can cause injury to personnel
and damage to equipment.
6. Alarm module OVERCURRENT
1. Set ENGINE CONTROL switch to
amber indicator flashes. TQG
disconnects from load.
2. Set DEAD CRANK SWITCH to
3. Set Battery Disconnect Switch to
4. Check load connected to TQG to see
Repair cause of overcurrent or notify
if there was a problem there that
could cause TQG to go overcurrent.
Inspect cables to load for shorts,
broken insulation, exposed wires,
signs of overheating, or failed
5. Determine if load is too large for
Reduce load as necessary.
generator set. (Power requirement
cannot be larger than TQG rating.)
6. Set Battery Disconnect witch to ON.
7. Set DEAD CRANK SWITCH to
8. Set ENGINE CONTROL switch to