200 kW TACTICAL QUIET GENERATOR SET
OPERATION UNDER USUAL CONDITIONS Continued
PARALLEL UNIT OPERATION (LOAD SHARING) Continued
Remove paralleling cable from storage box located inside battery compartment access door.
Connect paralleling cable between connectors on PARALLELING RECEPTACLES panels (WP 0005, Table 7).
10. Connect generator sets to load observing proper phase polarity.
Do not close the AC CIRCUIT INTERRUPTER switch on either of the generator sets, nor close the
load contactor at load until specifically directed to do so. Closing any of these devices at any other
time may severely damage one or both of the generator sets.