DESCRIPTION AND USE OF OPERATOR CONTROLS AND INDICATORS Continued
RECONNECTION BOARD TB1
OPERATORS ARE NOT AUTHORIZED TO REPOSITION THIS BOARD. Table 9 describes the Reconnection Board
TB1 located at right rear upper left of generator set (WP 0002 00, Figure 1, sheet 2).
Table 9. TQG Reconnection Board TB1.
Reconnection board top plate can be positioned to provide 120/208 Vac, 3-phase, or
240/416 Vac, 3-phase, power output from TQG set. Aligned arrows determine
Contains 12 connector lugs for ΦA,ΦB, ΦC, and neutral legs (L1, L2, L3, N or GND)
for 3-phase power output. Voltage output is for three-phase power.
Setting for 120/208 Vac, 3-phase, power output. Each phase is nominal 120 Vac to
ground and 208 Vac between any two phases.
Setting for 240/416 Vac, 3-phase, power output. Each phase is nominal 240 Vac to
ground and 416 Vac between any two phases.