200 kW TACTICAL QUIET GENERATOR SET
DESCRIPTION AND USE OF OPERATOR CONTROLS AND INDICATORS Continued
GENERATOR SET CONTROL Continued
Table 2. Generator Set Control Controls and Indicators Continued.
phase can be viewed one at a time by pushing AC METER key (14)at bottom of
GSC. Upper display also displays diagnostic codes for system faults. Refer to
Keypad descriptions (13 thru 19) for more information.
Active during paralleling only.
In paralleling modes, upper display toggles between bus and incoming generator
phase C-A voltage and frequency. Right side display shows bUS or GEn. Pressing
AC METER key (14) stops cycle.
When POWER METER key (13) is pressed, displays values for power metering.
When ENGINE METER key (15) is pressed, displays system battery voltage, engine
hours, engine speed, engine oil pressure, and engine coolant temperature. Each
value is shown for two seconds. A small pointer that lines up with the icon for the
condition indicates the value shown. Refer to Keypad description for more