200 kW TACTICAL QUIET GENERATOR SET
DESCRIPTION AND USE OF OPERATOR CONTROLS AND INDICATORS Continued
ELECTRONIC MODULAR CONTROL PANEL Continued
Table 1. Tactical Quiet Generator Electronic Modular Control Panel Controls and Indicators Continued.
Three-position toggle switch.
Up momentary toggle activates circuits to close load contactor. Connects TQG
Press-to-test green indicator is lit when load contactor is closed.
Toggle switch spring loaded to return to this position.
Down momentary toggle activates circuits to open load contactor. Disconnects
TQG from load.
Press-to-test green indicator is off when load contactor is open.
Press-to-test green indicator
Indicator lights when AC CIRCUIT INTERRUPTER switch is set to CLOSED.
Indicator off when AC CIRCUIT INTERRUPTER switch is set to OPEN.
PUSH TO STOP
Press for emergency stop of TQG. Switch pulled out for normal operations.
Switch can be reset by turning knob to right and pulling out.
BATTLE SHORT switch
Two-position toggle switch. Hinged red safety cover must be raised to set to
Disables all safety or protective devices except short circuit and overspeed.
Disables starting of engine. Yellow LED on GSC is lit.
Normal operation of generator set. Lowering red cover returns switch to OFF.
ENGINE CONTROL switch
Four-position rotary switch.
Engine shuts down and fault indicators and overload/short circuit module are
reset, except in emergency stop while EMERGENCY STOP pushbutton is in.
Allows remote start/stop control.
Starts and runs generator set diesel engine.
Shuts engine down after 5-minute cool down period has passed.
AUX FUEL switch
Two-position switch controls auxiliary fuel pump.
Turns on auxiliary fuel pump to supply fuel from external fuel supply.
Only allows fuel to be consumed from generator set fuel tank.