200 kW TACTICAL QUIET GENERATOR SET
DESCRIPTION AND USE OF OPERATOR CONTROLS AND INDICATORS
The following paragraphs contain references and illustrations that show the location and function of each control and
indicator for operation of the TQG. Each control and indicator is clearly labeled as it appears on the equipment. Call-out
numbers on the illustrations are keyed to the tabular listing which contains the name, based on the panel markings, and the
functional description of each control and indicator.
ELECTRONIC MODULAR CONTROL PANEL
Table 1 describes the controls and indicators located on the TQG Electronic Modular Control Panel (EMCP). The EMCP
includes the Generator Set Control (GSC) (1), Digital Voltage Regulator (DVR) (10), and alarm module (9). These three
components are illustrated and described separately in this work package.
Table 1. Tactical Quiet Generator Electronic Modular Control Panel Controls and Indicators.
GSC display module
GSC monitors generator operation and controls engine speed to maintain a
constant 50 or 60 Hz output, regardless of load. Refer to Table 2 for controls
Two-position toggle switch.
Control panel lights are lit.
Control panel lights are out.
Fuel level gauge
Indicates fuel level.