UNIT (FIELD) LEVEL MAINTENANCE
TACTICAL QUIET GENERATOR 100 kW, 50/60 Hz MEP-807A/PU-807A
AIR CLEANER SYSTEM MAINTENANCE
Tools and Special Tools
Tool Kit, General Mechanic's (WP 0119, Item 1)
Metal jewelry will conduct electricity. All jewelry can become entangled in generator set
components. Remove all jewelry when working on generator set. Failure to comply can cause
injury or death to personnel by electrocution.
DO NOT wear loose clothing when performing checks, services and maintenance. Failure to
comply can cause injury or death to personnel.
High voltage is produced when this generator set is in operation. Make sure unit is completely shut
down and free of any power source before attempting any repair or maintenance on the unit.
Failure to comply can cause injury or death to personnel.
High voltage is produced when the generator set is in operation. Never attempt to start or
maintain the generator set unless it is properly grounded. Failure to comply can cause injury or
death to personnel.
DC voltages are present at generator set electrical components even with generator set shut
down. Avoid shorting any positive with ground/negative. Failure to comply can cause injury to
personnel and damage to equipment.
When running, generator set engine has hot metal surfaces that will burn flesh on contact. Shut
down generator set, and allow engine to cool before performing checks, services, and
maintenance. Wear gloves and additional protective clothing as required. Failure to comply can
cause injury or death to personnel.
All fittings and openings must be capped or plugged immediately after opening to prevent